Monophase and Three-phase Pressure Booster Sets – Booster Pump MiniDAF
MiniDAF booster sets, domestic water or facilities prepared for pressurized water needs, silent running, fully automatic, comfortable, package booster.
TankTanks are used in European safety standards (CE). MembrThe membrane inside the tank conforms to German hygiene standards, It does not smell in water and does not produce bacteria. IhazThe device is equipped with a cable with a plug at the with level switch (5 m cable) against waterless operation are delivered.
Tahrik It can be driven by three-phase and single-phase motors. IfElectric control panel in standard manufacturing for three-phase models It is located. In single-phase models, electricity is optional. control board can be added.
MaksimumMiniDAF series pressure booster maximum permissible pressure 8 bars. If the mains pressure connected to the installation is high-pressure circuits, booster pressure line the booster must be protected by installing a check valve on it.
TECHNICAL specifications Booster Pump MiniDAF
|Suction Flange||1" 1/4 – 1"|
|Discharge Flange||1" 1/4 – 1"|
|Flow Range||1 – 10 m³ / h|
|Head Range||10 – 70 m|
|Max Fluid Temperature||40°C|
SCOPE OF APPLICATION Booster Pump MiniDAF
- Drinking water supply
- Process water supply
Pressure Increase Unit (Water Booster) – Booster Pump MiniDAF
Determination of pressure limits: First, the pressure of water booster required for all structure is determined. If the pressure higher than pressure allowed for flats occurs, problems occur in water use at flats and devices. In order to prevent this, pressure reducers are used
Water Pressure Booster Zones – Booster Pump MiniDAF
- If there is more than one pressure zone at the building, separate water pressure booster selection is made for each zone (Figure 3-a). First investment cost is high and energy saving is high.
- If there is more than one pressure zone at the building, feeding can be made with one water pressure booster; one pressure reducer is used for lower pressure zone. According to Figure 3-b, first investment cost is low and energy saving is high.
- If there is more than one pressure zone at the building, water supply be made with one water pressure booster, separate pressure reducer is used for each consumption section. According to Figure 3c, first investment cost is low and energy saving is high